A-Team Services Heating & Air has serviced the heating, cooling, indoor air quality and water heater needs Kennesaw GA since 1999.
Call us now at: 770 516-5165 or check out what your neighbors say about our heating and air conditioning repair and replacement services in Kennesaw GA.
for Kennesaw, GA
Our Reviews by City
Andrew - Kennesaw, GA
Alec was awesome. Great service and very informative.
Outstanding service, fantastic price!
Don - Kennesaw, GA
A+ for the A-Team!!! Greg and his team handled this job professionally and completed it the same day....faster than originally estimated. They installed two new AC units and two new furnaces. They did a great job with the install and cleaned up after they were finished. They were very friendly and easy to work with. The owner's brother - Greg was part of the team doing the install. He showed me how to change the batteries on the new thermostats and how to program them as well. Greg and his crew make you feel like family. You won't find a more honest and dedicated team that has the knowledge and expertise than these guys do and for the price I paid, they can't be beat. (Please know I made the purchase before the end of March when they offered a free furnace special with the purchase of a new a.c. unit). I recommend them to anyone looking for a new HVAC system. By the way my wife and I purchased the annual service plan and the first year is free. How about that! PS I'm not related to anyone that works at A-Team. They aren't paying me to say this. I'm just being an honest consumer that appreciates an honest Company doing an honest day's work.
Robert - Kennesaw, GA
Professional service! A++
Manning - Kennesaw, GA
The owner came out to see what my issues were. He gave me several options and explained all the benefits. His team came, installed and explained my new system. Highly recommended!!
Great service with affordable pricing.
Dawn - Kennesaw, GA
Since the insulation was added in July my home not only stays at a comfortable, even temperature but my electric and gas bill has dropped almost in half.
Janice - Kennesaw, GA
Service person arrived in a timely manner and was very professional.
Troy - Kennesaw, GA
Very knowledgeable and professional Bill is and the company has an awesome customer service staff!
Excellent Service..Friendly People
Susan - Kennesaw, GA
I've used A-Team for years and have always been highly satisfied. Very knowledgeable, always on time, friendly, and honest. Would recommend to everyone!
PB - Kennesaw, GA
I have used A-Teams services for many years now and have been pleased with my service every time. They are always on time, giving you a call 15-30 mins before arrival!
Friendly, Trustworthy Service
Brackett - Kennesaw, GA
Jane - Kennesaw, GA
Cecilia - Kennesaw, GA
Great service nice technician awesome price
Carol - Kennesaw, GA
Heater furnace heat maintenance
Installed american stand + dean pan w/ float switch 16x25x1 filter rack
Heat furnace heater maintenance
Installed 3 ton Lennox furnace with a 16x20x1 filter rack.
Service Agreement Fall tune up on a Rudd furnace with manual dampers
No heat on rheem furnace. Blower capacitor changed recently. Blower motor is locking up, and won't start once shuts off. Wired motor direct to 120vac to give customer heat for now. Need to order motor and replace.
Heat maintenance on new rheem furnace. Nest thermostat. 14x25x1 filter changed.
Heat, heater, furnace maintenance
Heater, furnace, heat maintenance
Added 1 s/a vent to garage + 1 bath vent
Run new t stat wire + repriced 2 t-stst (5000)
Heater maintenance. Furnace maintenance. Hest maintenance.
Heat maintenance. Furnace maintenance.
Found loose connection on American standard 80% 80000 BTU furnace rewired all working good
Found badd control board on Rheem 80% single stage gas furnace
Serviced a no cool in Kennesaw for exact comfort. We added 4 lbs. of 410a refrigerant to the system and did a leak search.
Service Agreement fall tune-up on Goodman system.
Furnace maintenance on a goodman system, with a white rodgers thermostat. Changed 16x25x1 filter. Heat was operating appropriately.
Estimate on an American standard 21" furnace
Air conditioning repair on Amana equipment
Air conditioning maintenance on American Standard equipment
AC tune-up on a Lennox full system with a Honeywell two zones
Adding R22 refrigerant to a Goodman heat pump zoning system to get them air conditioning with a one-week-old baby
No cool on a Rheem gas furnace air conditioning system
Found bad high limit on Trane furnace. Ordering part and rescheduling to replace.