A-Team Services Heating & Air has serviced the heating, cooling, indoor air quality and water heater needs Vinings GA since 1999.
Call us now at: 770 516-5165 or check out what your neighbors say about our heating and air conditioning repair and replacement services in Vinings GA.
for Atlanta, GA
Our Reviews by City
Great service and tech reps
Carol - Atlanta, GA
Always on time, competitive pricing and considerate of any issues. A ten year customer.
Todd - Atlanta, GA
Great service by tech
Barbra - Atlanta, GA
Great service by tech
Great service during the holidays
Ms Lisa - Atlanta, GA
The day before Thanksgiving my package Unit on the roof of my condo went out. A team came that day and gave me the bad news , it could not be fixed, replacement was necessary. A long story short, my new unit was installed with a crane no less without ruining my holiday or my bank account! Thanks A team!
Always quick and thorough
Maggie - Atlanta, GA
William - Atlanta, GA
bell - Atlanta, GA
I have a trust with A Team. They do what needs to be done; and don't take advantage.
allen - Atlanta, GA
The A-Team responded quickly to my service request, and the service technician, Greg, was friendly and very professional, quickly resolving my AC problems and clearly explaining to me the costs associated with the service. The A-Team and Greg were indeed my heroes on a hot summer day.
Excellent Updates/Repairs Services and Recommendations
Edward - Atlanta, GA
Jeff, arrived in an on time manner (called 30 minutes prior to actual arrival). He wore foot coverings to protect our floors. While performing routine semi-annual service, noticed three necessary repairs/upgrades. Discussed cost of each. Prices sounded good. Had parts/supplies with him and immediately did the work. No need to schedule another visit. Did the work right then. I look forward to the next semi-annual visit by Jeff or another team member. Jeff, keep up the great work! You are an asset to your company. Thanks. Ed and Colleen
8 years of Great Service
Terry - Atlanta, GA
We've been using A-Team for years and they are top quality people, year in and year out. Product, Services & pricing are great but mostly they are just good people that care about the quality of their work and about their reputation and it shows.
Arlene - Atlanta, GA
They rock! Always on time, always helpful! Great service!
Bell - Atlanta, GA
Terrific Service Once Again!
Rob - Atlanta, GA
A-Team Services has always done a fantastic job taking care of my HVAC Unit. Jeff was on time today, friendly, and knowledgeable. It's a pleasure to do business with this company!
Brad - Atlanta, GA
Jeff knew exactly the issue and was able to resolve quickly. Also provided realistic advice and options without a sales pitch which is much appreciated!
Great Service by Jeff Kurtz
Kaye - Atlanta, GA
Jeff did an excellent job in providing quality service. He is an excellent representative for his Company and was prompt, informative and professional.
2 system tune ups on Trane and Amana heatpump
Installed warranty evap coil
Service Agreement Fall tune up on a trane system
Installed new circuit board and high temperature limit in a carrier furnace.
Acid washed condenser coil for service agreement customer.
Heat tune up on a ruud furnace. Recommended blower wheel cleaning and a safety float switch. Changed 14x25x1 filter.
No heat on trane package unit. Blower motor wheel broken and needs repairing.
Swapped out honeywell 5000 thermostat for new honeywell 6000 programmable thermostat for a service agreement customer.
Pulled and cleaned blower wheel on an amana furnace
Found bad board on a Trane furnace
Service agreement tune-ups onto American Standard heat pumps
Don't hate tune up at Stephanie in Grant Bells place 1788 the cob Avenue Atlanta Georgia system checked out perfectly fine
Heat tune up on newly installed rheem furnace with high efficiency blower motor and honeywell smart touch screen thermostat.
No heat on a carrier air handler. Thermostat set to heat but needs to be in emergency heat or heat strips will not come on
Annual preventative maintenance on American standard airhandler heat pump system.
Bsd t-stat wire. Rewired with extra wire to give customer heat on a newly installed rheem furnace with aprilaire filter
No heat on air handler heatpump system. Unit has bad heat strip relay.
Heat tune up on a goodman furnace. Changed 16x25x1 filter.
Rewired inline float switchand reprogrammed honeywell 5000 thermostat auxiliary heat from comfort ro economy for an rheem airhandler/heatpump system.
No heat on trane furnace. Replaced a 15 uF blower motor capacitor and heat operating correctly.
Heat maintenance for two trane systems. Recommended blower cleanings on both. Changed 16x25x4 honeywell filter for main level. Need 20x20x4 honeywell for upstairs. Main level 90% furnace has water leaking from pvc flue pipe into furnace. Recommended redo flue pipe. Sealed bottoms of both furnaces to prevent air loss. Customer had a really cool dog.
Heat tune up on a new american standard variable speed gas furnace. Changed 16x20x5 Amana media filter. Nest thermostat. Heat operating well at this time.
Gas Furnace tune up on a carrier system. Changed 14x25x1 filter. Blower wheel has small dust buildup, otherwise operating correctly in heat.
Heat maintenance on a heatpump pack unit with electric heat strips in a closet. Changed 12x27x1 filter for service agreement customer.