A-Team Services Heating & Air has serviced the heating, cooling, indoor air quality and water heater needs Vinings GA since 1999.
Call us now at: 770 516-5165 or check out what your neighbors say about our heating and air conditioning repair and replacement services in Vinings GA.
for Atlanta, GA
Our Reviews by City
Great service and tech reps
Carol - Atlanta, GA
Always on time, competitive pricing and considerate of any issues. A ten year customer.
Todd - Atlanta, GA
Great service by tech
Barbra - Atlanta, GA
Great service by tech
Great service during the holidays
Ms Lisa - Atlanta, GA
The day before Thanksgiving my package Unit on the roof of my condo went out. A team came that day and gave me the bad news , it could not be fixed, replacement was necessary. A long story short, my new unit was installed with a crane no less without ruining my holiday or my bank account! Thanks A team!
Always quick and thorough
Maggie - Atlanta, GA
William - Atlanta, GA
bell - Atlanta, GA
I have a trust with A Team. They do what needs to be done; and don't take advantage.
allen - Atlanta, GA
The A-Team responded quickly to my service request, and the service technician, Greg, was friendly and very professional, quickly resolving my AC problems and clearly explaining to me the costs associated with the service. The A-Team and Greg were indeed my heroes on a hot summer day.
Excellent Updates/Repairs Services and Recommendations
Edward - Atlanta, GA
Jeff, arrived in an on time manner (called 30 minutes prior to actual arrival). He wore foot coverings to protect our floors. While performing routine semi-annual service, noticed three necessary repairs/upgrades. Discussed cost of each. Prices sounded good. Had parts/supplies with him and immediately did the work. No need to schedule another visit. Did the work right then. I look forward to the next semi-annual visit by Jeff or another team member. Jeff, keep up the great work! You are an asset to your company. Thanks. Ed and Colleen
8 years of Great Service
Terry - Atlanta, GA
We've been using A-Team for years and they are top quality people, year in and year out. Product, Services & pricing are great but mostly they are just good people that care about the quality of their work and about their reputation and it shows.
Arlene - Atlanta, GA
They rock! Always on time, always helpful! Great service!
Bell - Atlanta, GA
Terrific Service Once Again!
Rob - Atlanta, GA
A-Team Services has always done a fantastic job taking care of my HVAC Unit. Jeff was on time today, friendly, and knowledgeable. It's a pleasure to do business with this company!
Brad - Atlanta, GA
Jeff knew exactly the issue and was able to resolve quickly. Also provided realistic advice and options without a sales pitch which is much appreciated!
Great Service by Jeff Kurtz
Kaye - Atlanta, GA
Jeff did an excellent job in providing quality service. He is an excellent representative for his Company and was prompt, informative and professional.
Added 2 lbs R-22 to a a Carrier air conditioner with Goodman coil.
Air conditioner tune-up on a 5-ton Lennox system with two zones
Air conditioner maintenance on a Carrier heat pump system
Air conditioner maintenance on a newly-installed Rheem system. Found bad 10 inch motorized damper. Need to reschedule to replace motorized damper.
Air conditioning maintenance on a Friedrich/First Company closet package heatpump system. Changed 16x25x1 filter
No cool on a horizontal Amana system. Had impacted filter and dirty condenser
2 system air conditioning tune-up on high efficiency Trane 14 seer 410a systems. Recommended replace both capacitors and acid wash both condensers.
Two system air conditioner tune-ups on Goodman systems
No cool on a Trane R-22 system. Found blown 5 amp fuse, replaced, and air conditioning now operating properly.
No cool on a First Company water source heatpump unit. Low on R-22, previous leak found in evaporator coil. Added 4 lbs refrigerant, system now cooling. 63� supply air, 81� return air.
Air conditioner tune-up on a Lennox R-22 heatpump system. Changed 18x20x1 filter.
Found refrigerant leak while working on Amana air handler. Need to return to perform leak repair and recharge with 410a.
Air conditioning tune-up on Trane heat pump system. Changed 20x20x1 filter
No heat on a Trane furnace. Gas valve is sticking, and control board is dropping voltage intermittently. Has previously bypassed high limit inside furnace. Recommended do not run in heat as a safety precaution. Left estimate for new 4 ton Rheem and American standard full systems both 14 and 16 seer.
Working on an American Standard 2 and 1/2 ton heat pump system on a commercial high-rise
Found bad blower motor on a 2 ton on Fredrick system
Cleaning dryer vent
Two system air conditioning tune up on american standard and trane systems.
Air conditioning maintenance on American standard system with variable speed blower motor.
Heat and air conditioning tune up on a Rheem heatpump system with a hanging air handler. Left extra 20x20x1 filter
No cool on a York heatpump system. Bypassed board and ran 24 volts straight to reversing valve. 410a pressures good.
Two system air conditioning maintenance on american standard systems.
Estimate to replace hanging air handler/heatpump system. Install to be scheduled.
2 system furnace maintenance on American standard furnaces. Changed both 16x25x1 filters.